In accordance with ANSI/AIHA Z9.5, all chemical fume hoods must be equipped with a control (flow) monitor that can provide the user a real-time status of the fume hood's airflow. Some are more sophisticated than others including a digital readout displayed, other ambient measurements like temperature, and displayed error messages. Control monitors with digital displays must have a readout within 10% of the true airflow. Every control monitor should have a visual and audible alarm as well as a standard operation, or normal, status, typically represented with a green light.
Fume Hood Control Monitors
Control Monitor Standards
Chemical Fume Hood Control Monitor Manuals
Please access and obtain your chemical fume hood control monitor's manual below.
|Allen-Bradley PanelView 300 Micro|
|Crown Control Light Descriptions (manual unattainable, please review the rightmost image by right-clicking and opening in a new tab)|
|Fisher Scientific SAFEAIRE 54L0480|
|Mott Automatic Sash Operator 460|
|Phoenix Controls X30 Series|
|Rooster Monitor 100|
|Sentry Fume Hood Display by Phoenix Controls|
|TEL AFA 1000|
|TSI Alnor AirGard 335|
|TSI Alnor AirGard 405|
|TSI Sureflow 8650|